The UNITED Fire Systems CMA-1 is a device for monitoring the possible corrosion inside of a wet or dry sprinkler system piping. The assembly consists of a corrosion probe in a chamber, a pressure switch, an isolation valve, and a drain valve. The corrosion probe keeps pressure from reaching the pressure switch. When corrosion perforates the probe, pressure reaches the pressure switch, actuating a signal and providing early warning of possible corrosion inside the piping. The isolation valve allows replacement of the corrosion probe without depressurizing the entire system, and the drain valve safely vents pressure from the probe chamber.
The FM Approved United Fire Systems Model AR-1 Wet-Pipe Fire Sprinkler System Air Vent is a device for automatically releasing the trapped air from the high point(s) of a wet sprinkler system. Trapped air contains oxygen, which, when combined with water, is the primary cause of internal pipe corrosion. This corrosion can lead to pipe blockage, leaks, and pipe failure. The Model AR-1 Air Vent is installed at the system high point(s). Air is vented until water reaches the internal float valve, which automatically closes the device to prevent water release.
The FM Approved UNITED Fire Systems Pressure Maintenance Device Model NAMD-1 is a device designed to automatically regulate and maintain the flow of air or nitrogen into dry-pipe or preaction sprinkler pipe. The air or nitrogen pressure flows through a regulator so that upon activation of a sprinkler head, the air or nitrogen pressure will not interfere with the operation of the sprinkler valve or lengthen the time until the piping fills with water.
The UNITED Fire Systems Riser-Mount Air Compressor Model RMAC-LP is a device that automatically provides compressed air for preaction fire sprinkler and dry-pipe fire sprinkler systems. These single phase compressors are equipped with an electric motor, oil-less pump, compressor control pressure switch, relief valve, and bracket kit to mount the device directly onto the sprinkler riser above the preaction or dry-pipe valve. It can also be floor- or wall-mounted.
Your dry-pipe or preaction fire sprinkler system can be infected! That’s right – microbes can be lurking inside your sprinkler pipes and causing damage. Microbiologically influenced corrosion (MIC) occurs when the right combination of moisture and microbial organisms produces rapid corrosion of steel piping from the inside out. MIC is not the only cause of steel pipe corrosion, but it is important to know about and mitigate this problem BEFORE it causes pitting, pinholes, and thinning of pipe walls. Take steps to prevent both rust and MIC by using NITROGEN-PAC™.