The interior of preaction and dry sprinkler piping is subject to corrosion, which can lead to clogged sprinkler heads, leaks, and pipe failure. This corrosion can be of two distinct types. Oxidation corrosion takes place in the presence of oxygen and is accelerated by the presence of water. Microbiologically influenced corrosion (MIC) takes place in the presence of certain microbes that attack metal, again in the presence of water and in many cases oxygen. Reducing the damaging effects of this corrosion is best accomplished by greatly reducing or eliminating the amount of water and oxygen left in the pipe.
Ordinary air compressors that are used to provide supervisory pressure keep the oxygen concentration inside the pipe the same as normal air—ideal for oxidation corrosion to take place. Ordinary compressors also do not dry the air—residual water system testing remains in low points, and moist air can actually increase standing water within pipes from condensation. The introduction of high-purity dry nitrogen with a low dew point reduces or eliminates these two problems. The interior of the pipe remains dry, with very little oxygen remaining to attack the metal.
Contact Our Team
You're looking for expertise and quality. That's where we come in.
Did You Know?
If you have a dry standpipe in your structure, can you tell if it’s intact and ready for fire department use? If it’s not, the risk is high. Be sure – a UNITED Fire Systems STANDPIPE-PACsystem will alert you if someone accidentally leaves a valve open or even disassembles a portion of the standpipe inadvertently.